This pump vault filter became so clogged that it actually began to collapse in on itself.
A clogged Biotube® and a clean one. The clogged filter was found only after a pump had burned out.
This system became so root infested, it required the Drain Field to be replaced. Inspections and preventive maintenance could have saved it.
This system had not been cleaned or pumped until it was discoved that the sewage had broke out at the surface and the owner could no longer flush his toilet.
A leaky, cracked and broken tank.
This Drain Field became so backed up it required extensive repair.
This high schools system failed so dramatically that it flooded the entire pump vault. Had it gone unchecked any longer the effluent would have shorted out the entire control system. (green box)
Copyright 2000 - 2005 © - All rights reserved Affordable Septic Systems - product images provided and copyright by Orenco Systems ® and used by their permission. If you have questions about this site or encounter errors please contact us at email@example.com